Not feeling heat and receiving error code 228 from your Lennox® furnace?
This shows your heating system couldn’t adjust its pressure switch before turning on. As a reaction, your system will not run for your protection.
Repairing or replacing this part is best left to the Experts at Stark Services in Haltom City. Our NATE-certified technicians are among the brightest in the industry. They’re well-prepared to work on all of your heating needs, including clearing a furnace error.
We want you to be absolutely satisfied with our quality furnace repair in Haltom City. That’s why we back it with a 100% Satisfaction Guarantee* for a year.
How a Pressure Switch Works
This part plays a prominent part as your furnace prepares to work in your house.
Here’s what goes on after your thermostat’s call for heat:
- Your furnace’s control board starts running the draft inducer blower motor. This drains combustion gases from the heat exchanger and pulls in new gas and air so the burners can fire.
- When the pressure switch senses that plenty of air is being pulled into the burners, it closes and signals the control board to ignite the furnace.
- Your furnace ignites and provides heat.
What Happens When a Pressure Switch Fails
When your pressure switch isn’t functioning promptly, you’ll likely hear the fan going and the switch clicking multiple times before the furnace turns off completely. When a part isn’t working right, your furnace will turn off to protect you.
Your furnace will tell you something is amiss with a red flash from its indicator light, which it uses to exhibit error codes. It uses this red light to flash code, like Morse code.
You may see short flashes or an alternating slow flash as it transmits a fault code.
Estimated Repair Cost for Furnace Error Code 228
Before replacing the switch, your Stark Services Expert will investigate other parts of your furnace first. Several other issues can also create the error code, like a congested vent or cracked hose.
The cost to repair your furnace depends on the issue with it and how long it takes to fix it.
If your pressure switch needs to be replaced, you can anticipate to pay between $40 to $350.
Start with the Experts at Stark Services
If you need furnace repair, reach out to the technicians from Stark Services to check out the fault code and fix the problem to your satisfaction.
Call us at 817-668-6689 or schedule an appointment online today.